I am installinga bank of 8 GFCI blank gFCI receptacles at the home run end of an underground conduit. None of them pass current to the load. I swapped out one of them with a normal GFCI receptacle and it worked just fine. I checked the load/line wiring three times to be sure I was not drunk, and it's fine. Reset test does nothing. The line terminals are cold. Any thoughts????????