1 Reply Latest reply: Mar 20, 2013 12:01 PM by Rob Ramirez
I have a PR180 switch in a 3-way circuit that I am having trouble with. Specifically, the 3-way switch at the other switch location does not turn the light on, even with the supplied jumper installed. I have reviewed the installation instructions available in pdf format on this site, and they are confusing. The instructions mention "jumper wires;" does this mean that more than one jumper wire is required for proper installation? Also, the wiring diagram in the instructions shows the regular 3-way switch at the location of the hot line; in my situation, the PR180 is at the hot line location and the regular 3-way switch is at the load location. I have read that there may be two different versions of the PR180: an older version with a solid yellow wire, and a newer version with a wellow/red wire. If it makes any difference, mine has the yellow/red wire.
Thanks in advance for any assistance provided.